Automatic Fire Water Cannon Fire Door Monitoring System Fire Equipment Power Monitoring System Electrical Fire Monitoring Alarm System Recoverable Optical Fiber Differential Temperature Fire Detection Fire Emergency Lighting and Evacuation Indication System
They have always supported Jiangsu Ziqiang Technology
Manager Lin: 189-5110-0117
Manager Chen: 133-8218-2119
Address: No. 206 Yandangshan Road, Suzhou High-tech Zone
ZDMS0.6 / 5S smart water cannon has a high fire and fire extinguishing performance and is widely used in many domestic construction projects. It can be installed between 6-22m, can be installed on a ceiling or can be installed on a corner or a wall. side. When it is located near the wall, the distance between the ZDMS0.6 / 5S smart water cannon and the wall is about 50 cm, so it will not affect the normal operation of the water cannon. When installing, make a water cannon bearing bracket and fix the water cannon. Location. Basically, the water cannon is installed and then renovated. The pipeline layout of the ZDMS0.6 / 5S intelligent water cannon can be constructed according to the fire design drawings. The equipment wiring of each manufacturer is different, and can be performed according to the corresponding manufacturer's equipment. For wiring, the on-site control box should be installed at a height of about 1.5m from the ground and where the water cannon can be seen.
First, ZDMS0.6 / 5S intelligent water cannon system wiring
(1) Water monitor to the field area control box: RVV3x1.5 (water monitor power line 220V) + RVSP2x1.5 (water monitor control line)
(2) Solenoid valve to the field area control box: RVV2x1.5 (solenoid valve power cable)
(3) On-site area control box to end water test device: RVV3x1.5 (power cable of end water test device) + RVSP2x1.5 (signal total
(4) On-site area control box to fire alarm host: RVV3x2.5 (power line) + RVSP2x1.5 (signal total
Line) + RVSP2x1.5 (remote control line)
(5) Water cannon to fire alarm host: SYV-75-5 (video cable). (When the water cannon does not have video, video and remote control are not required.
Line, the system does not have remote control function)
(6) Fire alarm host to pump room: RVV4x1.5 (start pump line, start pump feedback line).
Note: All control and signal cables in this system should use twisted-pair shielded cables. This cable is a weak current cable and cannot be connected with a solenoid valve
The power cables are laid in a common tube. When using cable trunking, separate cable trunking must be used.
ZDMS0.6/5S智能水炮及电磁阀接线 Second, ZDMS0.6 / 5S intelligent water cannon and solenoid valve wiring
The water cannon's own cable is about 1.5 meters long (of which the 3-core cable is the power cord, red fire wire, black neutral wire, yellow ground wire; double
Twisted wires are control wires, red is positive, black is negative). When connecting with additional cables, each wire end must be insulated and packaged separately after welding.
Wrap and make a color record. (The company is equipped with a 220V to 12V in-line camera power adapter, which can be connected with the water monitor power cord.
Previous: What are the Jiangsu Ziqiang fire cannons?return